If you don't get an e-mail with your access data, please make sure that you have already registered with us. As soon as you are registered, you can login with your e-mail address and your password.
If you have forgotten your password you can create a new one using the form below.
|General||The fan can be operated with a regular light switch.|
|Timer||After the fan is switched off, it will continue to run for the set lag time and turn itself off automatically. This lag time can be set manually to between 2 and 30 minutes. Two power supplies - one continuous and one switched - are required.|
|Ball bearings||An additional ball bearing is particularly recommended for ceiling applications. This extends the fan's service life and reduces the operating noise.|
|Humidity sensor||If the humidity in the room exceeds a the set value, the fan will automatically switch on and run until the humidity drops below the set value, at which point it will switch off automatically. The built-in humidity sensor can be adjusted for humidity levels between 60% and 90%.
With integrated lag time, the fan will continue to run for a set time. At least one continuous current is required for this operation. An optional second switched current can be used to switch the fan on/off separately.
|Ø 4" (100mm)||100||152||120||126||30|
|Ø 5" (125mm)||125||177||140||135||34|
|Ø 6" (150mm)||150||206||165||154||36|
|Ø 4" (100mm)||Ø 5" (125mm)||Ø 6" (150mm)|
|Airflow per hour [m³/h]||88||167||265|
|Noise level at 3m [dB/3m]||33||34||37|
|Maximum static pressure [Pa]||33||50||78|
|Power consumption [W]||14||16||24|
|Supply voltage [V/Hz]||230/50||230/50||230/50|
|Maximum operating temperature [°C]||45||45||45|
|Index of protection [IP]||34||34||34|
|Rotations per minute [1/min]||2300||2400||2400|